Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
This alarm means that the trip unit hardware has lost its time. This alarm is part of the default MicroLogic device profile and will be added to each MicroLogic device added to the system unless a custom profile is created without it.
To clear this alarm condition, the user can write a 1 to the Device Date/Time reset tag--LPHD1\ZRsDateTm\ctlVal. This will sync the trip unit's clock to the server time.
If the user is not interested in receiving this alarm, it can be disabled or the alarm tag and variable tag can be deleted from the system.
Keywords: PLS, PLSCADA, PL SCADA, Power SCADA, StruxureWare PowerSCADA Expert, SPE 7.1, 7.2, 7.10, 7.20, micro logic, tripunit