Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
The PM800 meets IEC620583 which dictates that the minimum pickup current is 5 mA. There must be a minimum of 5 milliamps current on the CT secondaries (0.1% load with a 5 amp secondary, or 0.5% load with a 1 amp secondary) for the meter to begin metering current.
excitation, pickup, pick up, turn on, PM820, PM850, PM870, PM8