Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The user has a ION meter's analog output configured based upon Frequency. When there is no source voltage on the meter, the analog output value stays in the last known state instead of going to 0.
Facts and Changes
Any ION meter with an available analog output and an available arithmetic module.
Causes and Fixes
When there is no voltage at the metered terminals, the frequency is n/a. Because of this, the analog output registered the last known good value.
Follow the attached procedure to add logic to the output so that it displays 0 when there is no voltage present.