The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The user has a ION meter's analog output configured based upon Frequency. When there is no source voltage on the meter, the analog output value stays in the last known state instead of going to 0.
Facts and Changes
Any ION meter with an available analog output and an available arithmetic module.
Causes and Fixes
When there is no voltage at the metered terminals, the frequency is n/a. Because of this, the analog output registered the last known good value.
Follow the attached procedure to add logic to the output so that it displays 0 when there is no voltage present.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!