Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
In order to use 2-wire communications on a Micrologic Trip Unit:
1. The Micrologic trip unit must have a BCM (Breaker communications module) with gray terminals (If the device has green terminals on the BCM it is not capable of the 2 wire communications configuration)
2. A Micrologic trip unit type P or H with date code 11351 or higher
The Micrologic trip unit may be set to 2 wire from the front display of the trip unit or by using the Micrologic RSU software. Please see the attachment for a detailed description on how to set the Mircrologic trip unit to 2 wire communications.
Note: If the BCM date code is 11351 to 12132, the user may see ComLoss errors in SMS. The user must either be running SMS 4.3 with the Micrologic patch or replace the BCM with date code 12132 or higher.