Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
A customer's OPC client will not connect to the ION server to export data. When checking the Windows Services list to be sure the OPC Service is started and running, or to perform a service restart, the ION OPC Data Access Server service is no longer in the list.
Checking the setuplog file shows an error similar to:
OK (0) 6/13/2012 3:58:40 PM ERROR Unable to stop service PMLOPC. Time out exceeded. Could not stop ION OPC Data Access Server within 60 milliseconds
OK (0) 6/13/2012 3:58:40 PM Removing service:PMLOPC
Causes and Fixes
The service can be registered manually:
Open a command prompt, and type 'ION.OpcDaServer.exe -Service' and the service will re-appear in the services list.