The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
A customer's OPC client will not connect to the ION server to export data. When checking the Windows Services list to be sure the OPC Service is started and running, or to perform a service restart, the ION OPC Data Access Server service is no longer in the list.
Checking the setuplog file shows an error similar to:
OK (0) 6/13/2012 3:58:40 PM ERROR Unable to stop service PMLOPC. Time out exceeded. Could not stop ION OPC Data Access Server within 60 milliseconds
OK (0) 6/13/2012 3:58:40 PM Removing service:PMLOPC
Causes and Fixes
The service can be registered manually:
Open a command prompt, and type 'ION.OpcDaServer.exe -Service' and the service will re-appear in the services list.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!