The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Facts and Changes
PRODUCTS Affected3710, 3720, 3750
Causes and Fixes
In order for the desired snapshot recorder to be selectable in the query wizard, the user must configure the sliding or thermal demand parameter. To do this, open the meter in Designer, select Demand, insert the non-configured parameter and then send it to the meter. The user will then need to re-create the tree file for the meter so the log inserter then pulls that data log.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!