Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Facts and Changes
PRODUCTS Affected3710, 3720, 3750
Causes and Fixes
In order for the desired snapshot recorder to be selectable in the query wizard, the user must configure the sliding or thermal demand parameter. To do this, open the meter in Designer, select Demand, insert the non-configured parameter and then send it to the meter. The user will then need to re-create the tree file for the meter so the log inserter then pulls that data log.