Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The Fundamental Phasor Readings Table in SMS displays incorrect values for a 3-Phase High-Leg Delta system, also referred to as: Red-leg, Stinger-leg, Center-Tap grounded, or Wild Leg. For a normal (3-wire) delta only L-L readings are available, however, a center tapped grounded connection delta system is considered to be a 4-wire system type (40 or 41 depending upon installation) and is treated as such by the meter. As such it is expected that the L-L voltage phases will have a 120 degree separation.
For a 3-phase 4-wire system (monitored by a PM800, CM3000, or CM4000), the fundamental phasor readings table will display L-N Voltages and not the L-L Voltages (Note, the neutral as shown is actually the ground). The A-N Voltage will have 180 degrees of separation from the C-N Voltage (assuming that B is the High Leg). Additionally, the B-N voltage (the high-leg) will have 90 degrees of separation for the other two L-N readings. See Figure 1 below for a typical example.