Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
In general, it is not possible or useful to change the output register measurement names for a single PowerLogic meter. This is because PowerLogic meters communicate to PME through translator files, unlike ION meters, which communicate directly to the system.
It is possible to modify the translator file to change the register name, but that change would be global across ALL meters of that type in the system.
For example, the B-S1 Status name in a CM4000 may be changed by editing the translator file, but that change would affect all CM4000s in the system.
Generally, this is not recommended.
Note about ION meters: Since the system has access to the framework of ION meters, register names for ION meters can be changed individually; however, this is not possible with PowerLogic meters.