Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
A customer may want to use the Analog Output Module of the ION meters to represent the power factor and feed the information to another device/system. However, the power factor ranges from -1 to 1 which doesn't map over to the Analog Output module. The Analog Output Module will only take a zero Source input value for its zero scale, one needs to find a way to put the power factor into a range starting with 0.
Causes and Fixes
Since power factor is a cos function of angle, one can use the Arithmetic module's "arccos" function to transform PF (1 to -1) to radius (0 to 3.141593). Then map the radius value to the 0-20mA or 4-20 mA input.