Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
A customer may want to use the Analog Output Module of the ION meters to represent the power factor and feed the information to another device/system. However, the power factor ranges from -1 to 1 which doesn't map over to the Analog Output module. The Analog Output Module will only take a zero Source input value for its zero scale, one needs to find a way to put the power factor into a range starting with 0.
Causes and Fixes
Since power factor is a cos function of angle, one can use the Arithmetic module's "arccos" function to transform PF (1 to -1) to radius (0 to 3.141593). Then map the radius value to the 0-20mA or 4-20 mA input.