Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
During the database upgrade required for SPM 7.0, a number of measurements were remapped to different IDs. If a report configured and saved prior to the upgrade from ION Enterprise 6.0 to Power Monitoring 7.0 referenced measurements that were remapped, the saved reports will lose their links to the selected measurements, resulting in the behaviour described. To correct this, it is necessary to re-select the desired measurements, i.e. reconfigure the report, and then re-save it.
This is most likely to happen with 100 ms reports using CM4000 data, and WAGES data.
Last Revised: March 19, 2012
All content © 1992-2012 Schneider Electric