Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The BCPM register list only contains register addresses for circuits 1-42. To read circuits 43-84 you will need to read the same registers for circuits 1-42 on the next modbus address. For instance if the BCPM is configured to modbus address 1, you will read circuits 1-42 exactly as the register list details. For circuits 43-84 you will read the same registers using modbus address 2. This principle also applied when adding an 84 circuit BCPM to an EGX or ECC card, you will need to add the configured address and the proceeding address.