Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
How to read registers for circuits 43-84 from a Branch Circuit Power Meter (BCPM or BCPMSC).
User wishes to read registers for circuits 43-84.
The BCPM register list only contains register addresses for circuits 1-42. To read circuits 43-84, the same registers for circuits 1-42 will need to be read on the next modbus address.
For example, if the BCPM is configured to modbus address 1, registers for circuits 1-42 will be read exactly as the register list details. For circuits 43-84, the same registers will also be read using modbus address 2.
This principle also applied when adding an 84 circuit BCPM/BCPMSC to an EGX or ECC card, the correct configured address and the proceeding address must be added.
For the list of registers for the BCPM/BCPMSC, see FA212184