Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
CM3000 Power Demand and Peak Demand are resetting on the 1st of the month when no scheduled tasks are set up.
Causes and Fixes
CM3000s with firmware 15.020 and below will experience this issue.
Register 6426 has a default setting to automatically reset peak demand at the beginning of the month. The default has been set to 3 to reset both power and input metering peak demand.
To stop demand from resetting each month:
Change the default value from 3 to 0:
write value 9020 to register 8000
write value 0 to register 6426
write value 1 to register 8001
write value 9021 to register 8000