The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The PowerLogic BCPM or BCPMSC shows 0A on every circuit, even though the panel the meter is monitoring has a load.
The meter has been installed correctly and all CT connections are made.
Causes and Fixes
If the ribbon cables are reseated while the BCPM is on, the unit will not register current.
The BCPM does a discovery of the ribbon cables only upon bootup.
If the ribbon cables are reseated or seated after bootup, the BCPM will not detect the current.
Cycle power to the meter with the ribbon cables attached.
If this still does not resolve the problem, there is a BCPM repair kit with catalog number BCPMREPAIR. An instruction manual is attached.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!