Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The PowerLogic BCPM or BCPMSC shows 0A on every circuit, even though the panel the meter is monitoring has a load.
The meter has been installed correctly and all CT connections are made.
Causes and Fixes
If the ribbon cables are reseated while the BCPM is on, the unit will not register current.
The BCPM does a discovery of the ribbon cables only upon bootup.
If the ribbon cables are reseated or seated after bootup, the BCPM will not detect the current.
Cycle power to the meter with the ribbon cables attached.
If this still does not resolve the problem, there is a BCPM repair kit with catalog number BCPMREPAIR. An instruction manual is attached.