The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Note: The E5600 takes into account the CT/PT multipliers when determining when to pulse.
To calculate the pulse weight value, first determine the highest kW value you can expect and the required pulse rate. In this example, the following assumptions are made:
The CT multiplier is 80, the PT multiplier is 4
The maximum load is 1600 kW.
One KY transition per second should occur at full scale.
Step 1: Convert the 1600 kW load into a primary energy value, then into kWh/second.
Primary Energy Value = (1600 kWh)(1 Hr)/(80*4) = 5 kWh (this is how much energy the meter sees)
5 kWh/1 hour = 5 kwh per 3600 seconds yields 0.00138 kWh/second
Step 2: Calculate the kWh required per pulse.
(0.00138 kWh/second)/(1 pulse/second) = 0.00138 kWh/pulse
Step 3: Round to nearest thousandth, since the meter only accepts 0.001 kWh increments.
Ke = 0.001 kWh/pulse
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!