The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
When trying to view Meters, Bar Charts, Tables, or Real Time Trends, "No Devices" populates where the list of devices should be.
Causes and Fixes
This can be caused when the SMS Configuration Utility is pointing to a different system than the one that's online.
1. Go to Start>Programs>PowerLogic>Tools>SMS Config Utility
2. Go to the Diagnostics tab.
3. Select the correct system name in the drop down box.
4. Restart the PowerLogic Network Server (PLNS) Service.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!