Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The Portable Circuit Monitor 2000 series has built-in potential transformers of a ratio of 600:120 V. To compensate for this 5:1 V ratio, the factory default PT ratio has been set to 120:24 V. This unusual voltage secondary of 24 V could be the cause of improper voltage readings.
If the customer wishes to change the voltage secondary back to the standard 120, they need to write the value of 120 to register 2008(range for this register is 1-600). Note that the native 5:1 V ratio must still be taken into account if the voltage secondary is changed. For a system with no PTs, the primary must also be changed back to 600 V.