The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
When running the ION_Diag diagnostics program, the following error is generated referring to MinDate and MaxDate properties and the program will not run.
Run-time error '35773':
A date was specified that does not fail within the MinDate and MaxDate properties.
ION Enterprise 5.5, 5.6
ION Enterprise 6.0.x
The error is a result of the transition to the year 2011. The Visual Basic form defines a MaxDate property for the date range desired for the system log which was set to 12/31/2010.
Download and extract the attached version of ION_Diag and transfer it to the ION server.
Run the new version of ION_Diag.exe.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!