The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The CyberScience SER-3200 device can receive an IRIG-B time signal from an external Arbiter GPS time source device. The SER-3200 requires an IRIG-B signal which includes both date and time information. Without the Arbiter device configured to include IEEE-1344 extensions, the SER-3200 will show a time quality of Good while having a good time but invalid date.
Causes and Fixes
The Arbiter time source device does not have IEEE-1344 extensions enabled.
Enable the IEEE-1344 time extensions on the Arbiter time source device.
Use the Arbiter time source device menu to verify IEEE-1344 extensions have been enabled.
For more information about the SER-3200 and IEEE-1344 extensions visit the CyberSciences website http://www.cyber-sciences.com/support/technical_irig-b.html
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!