Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The CyberScience SER-3200 device can receive an IRIG-B time signal from an external Arbiter GPS time source device. The SER-3200 requires an IRIG-B signal which includes both date and time information. Without the Arbiter device configured to include IEEE-1344 extensions, the SER-3200 will show a time quality of Good while having a good time but invalid date.
Causes and Fixes
The Arbiter time source device does not have IEEE-1344 extensions enabled.
Enable the IEEE-1344 time extensions on the Arbiter time source device.
Use the Arbiter time source device menu to verify IEEE-1344 extensions have been enabled.
For more information about the SER-3200 and IEEE-1344 extensions visit the CyberSciences website http://www.cyber-sciences.com/support/technical_irig-b.html