Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The CyberScience SER-3200 device can receive an IRIG-B time signal from an external Arbiter GPS time source device. The SER-3200 requires an IRIG-B signal which includes both date and time information. Without the Arbiter device configured to include IEEE-1344 extensions, the SER-3200 will show a time quality of Good while having a good time but invalid date.
Causes and Fixes
The Arbiter time source device does not have IEEE-1344 extensions enabled.
Enable the IEEE-1344 time extensions on the Arbiter time source device.
Use the Arbiter time source device menu to verify IEEE-1344 extensions have been enabled.
For more information about the SER-3200 and IEEE-1344 extensions visit the CyberSciences website http://www.cyber-sciences.com/support/technical_irig-b.html