Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
If there are no voltage readings on an ION8600, but other readings are available, it is likely the meter is stuck in Test Mode.
Verify with a fluke meter that there is voltage going into the meter. If there is, connect to the meter with ION Setup and place it into Test Mode and then exit out of test mode. The voltage readings will no longer be zero.
Date Created: November 12, 2010
Last Revised: November 18, 2010
Original Author: DD
All content © 1992-2010 Schneider Electric
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!