Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
A PM8 with an ECC module is able to send SNMP V2 Traps. Both Generic and Enterprise specific traps are supported. Generic Traps supported are defined within the private MIB SchneiderPm8eccV01_00.mib(for use with PM8ECC V2.300 and greater firmware) and include:
coldStart (0): The PM8ECC (containing the Agent) is reinitializing.
warmStart (1): The PM8 (which supplies Enterprise data to the agent) has reinitialized while the ECC continues to run.
linkup (3): The Agent interface has been Enabled.
authenticationFailure (4): An SNMP manager has sent an incorrect community string.
Enterprise Specific Traps include:
Priority 1 Alarm (1): The PM8 has detected an alarm with a configured priority of 1(HIGH).
Priority 2 Alarm (2): The PM8 has detected an alarm with a configured priority of 1(MEDIUM).
Priority 3 Alarm (3): The PM8 has detected an alarm with a configured priority of 1(LOW).
Every alarm enabled in the PM8 has a configured priority of 0-3, where 0=None and 3=High. If SNMP Traps are enabled in the PM8 a trap will be sent on the occurrence of an alarm with the associated priority. Within the trap details about the alarm are passed within the following trap variables:
Date/Time: Date and time the meter detected the alarm
Alarm Label: The name of the alarm as configured in the PM8
Alarm Priority: Priority of the detected alarm
Alarm State: The state causing the alarm as detected by the PM8. Supported States include:
Pickup Monitored quantity changing from a normal to alarm value
Dropout - Monitored quantity changing from a alarm to normal value
Diag - Diagnostic
Alarm Value: The value of the monitored quantity when the alarm state changed as measured by the PM8
The latest MIB template is available for download on http://www.powerlogic.com/downloads.cfm/cs/1
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!