Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Support for the PM750 was added in Service Update 3 for SMS Version 4.0. In SMS v4.0.2, PM750 devices in the system show Communication Loss alarms, even though the user can still read registers from the devices. The Error Code in the Activity Log associated to the Comm Loss alarms is 4008, which denotes an invalid "Square D ID". In other words, the PM750 is not supported in that version. Running the Service Update 3 install will upgrade SMS to version 4.0.3. At this version, the PM750 is fully functional and the Communication Loss alarms should clear.
Keywords: v4.0.3, SU3, PM7