Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Each integer register has a scale factor associated with it. See the following example below:
Data point needed: Current for meter 1 in a single phase, top feed configuration:
Data Register 1336: 8000
Scale Register 1000: 65,534 (which is -2 in 2s complement. Since 65534-65536=-2)
Formula: Data register * (10^scale register) = Scaled value
E.g. 8000*(10^-2) = 80 Amps
See the BCPM register list for more information and listing of all modbus points.