Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
This patch displays the APM alarm timestamp at the millisecond level for those alarms in SMS that are in millisecond format.
This patch is only intended for APM v 6.0, 6.1, and 6.2.
Default Format - 8/10/2010 11:46 AM
Format After Patch - 8/10/2010 11:46:22.110 AM
To deploy the patch:
1. Stop APM and OPC Logger services.
2. Rename the PLOpc.Common.dll in the [install location]\SMS OPC AE Server\ folder and in the [install location]\Active Pager Module\ folder.
3. Copy the included dll in the [install location]\SMS OPC AE Server\ folder and also in the [install location]\Active Pager Module\ folder.
4. Start the APM and OPC Logger services.