Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
When the status of a CM3/CM4 digital input changes, the change is not shown in SER. In addition, no errors are present in SER.
Causes and Fixes
The Circuit Monitor's input is incorrectly configured
Set the CM's digital input Mode to SER
Enable the CM's onboard SER Data Log with a non-zero record count.