The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
The default StatusRegister setting of 1100 will work with the Power Meter 600 in PowerLogic SCADA, even though 1100 is not defined in the PM6 Register List. If the user reads register 1100 with a generic Modbus register reader, he will receive a value of 32768. While this denotes an undefined value, the register is still readable and therefore, the PM6 I/O device can use this register as verification to come online.
The following is some additional general information about the StatusRegister parameter:
This parameter defines the address of the register that the driver will read to determine whether a device is responding to communication requests. The result of this read is not important; however, it must be a valid register address within the device. This parameter can only be configured for the PWRMODBUS driver.
Keywords: Series 600, PM600, PM620, PM650
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!