Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Branch Current Monitor (BCM) Orientation
The circuit orientation is determined by dip switch settings on the BCM board. Refer to the BCM Circuit Orientation.pdf document for dip switch settings.
Note: Changing the circuit orientation is only available on BCMs with a firmware revision of 1.10 or greater. The firmware revision number is stored in holding registers 50 and 51. For example if register 50 = 1 and register 51 = 9, the firmware revision is 1.9.
Branch Circuit Power Meter (BCPM) Orientation
The circuit orientation is determined by the value held in register 6.
0 = Top Feed (Default)
1 = Bottom Feed
2 = Sequential
3 = Single Row: Odd/Even
Refer to the BCPM Circuit Orientation.pdf document for register settings.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!