Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The tag with Real and Long data type is 2 words (4 Bytes) format. It is allowed to change the reading order of the bytes on PLS by change the parameter in citect.ini file for MODNET protocol.
Modnet20 is specified for TSX Quantum PLC ranges. These protocol options will select the correct addressing modes, select certain INI values and other settings to provide compatibility with these devices without the need to set any other special parameters. Base on the default setting, some of parameters cannot be changed. Therefore, it is recommended to use Modnet protocol.
Please use the parameter to change the byte order for Real data type
FloatMode = x where x is 0, 1, 2 or 3
0: Order of bytes = 1 0 3 2
1: Order of bytes = 3 2 1 0
2: Order of bytes = 0 1 2 3
3: Order of bytes = 2 3 0 1
Default Value: 0
In the MODNET protocol, LONG data types default to a simplified implementation, with a shortened range of 0 to 655,359,999 - mode 0. Mode 2 has the same range as mode 0, but with the register order swapped. Mode 1 supports the full LONG range of -2,147,483,648 to +2,147,483,647. Mode 3 has the same range as mode 1, but with the register order swapped.
When using the MODBUS protocol, CitectSCADA combines two registers to store a long data type in a PLC. The way in which it does this is defined by this parameter in the "citect.ini" file.
LongDataType = y where y is 0, 1, 2 or 3
0 - implies 10,000 * low register + high register
1 - implies 65,536 * low register + high register
2 - implies 10,000 * high register + low register
3 - implies 65,536 * high register + low register
Default Value: 3
Last Revised: 09 Apr 2010
Original Author: EF
All content © 1992-2010 Schneider Electric