Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
A customer has a data recorder depth set to 3360. When he uses ION Setup to display the logged data, only 3000 rows of data can be seen.
Causes and Fixes
By default, the data screen of ION Setup is set to display 3000 rows of data.
In order to display more data in the data screens of ION Setup, please follow the procedure below to modify the pml file: -
Step 1: Go to the device that requires editing in the folder ..\ION Setup\Tables (e.g. ..\Schneider Electric\ION Setup\Tables)
Step 2: Pick a data recorder table (e.g. ..\Schneider Electric\ION Setup\Tables\PML7650\Version 2.2 Default\Data Recorders\Historic Average.pml)
Step 3: Open the pml file with Notepad and modify the value of "ROWS" to a higher value (e.g. 3360)
Step 4: Save and close the file.
Connect the meter with ION Setup again and you should see the data screen for Historic Average should display a maximum of 3360 rows.