Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
When connecting to the E5600 meter for the first time, the energy pulsing cannot be properly enabled through optical port.
Causes and Fixes
As shown in the Figure below, KY Relay #1 and KY Relay #2 are enabled and the KT values have been defined. If communicating through Modbus the same screen will be shown below, indicating that the meter is ready to pulse through its Digital Output. The meter will not pulse until meter pulsing is enabled through the Modbus interface.
In the case of attempting to enable meter pulsing through the optical probe, and receiving no pulses from the digital output, follow the steps below to resolve the issue:
Step 1: Communicate to the meter via Modbus in ION Setup,
Step 2: Disable the KY Relay #1 and KY Relay #2 and press the send button
Step 3: Enable the KY Relay #1 and KY Relay #2 and press the send button
Please note: Make sure that a KE value has been selected.
(Removed Image URL: /PubResEXPORT.nsf/2b87ee90be777fc085257c28006ee4ef/4c7dd0f5c323696cc1257657001097d1/fl_block_5/0.1A60?OpenElement&FieldElemFormat=gif)
Date Created: October 19, 2009
Last Revised: October 21, 2009
Original Author: SN
All content © 1992-2009 Schneider Electric