Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
System Manager Software (SMS) will only scale by factors of 10, but there is a way around this by using a virtual circuit node and if necessary a meter with available utility registers. PM800s, CM3000s, and CM4000s all have a block of 200 utility registers starting at register 15,800. These are empty read/write registers that a user can use to store values.
User has a third party device such as Caterpillar EMCP (Electronic Modular Control Panel) which uses non-standard scaling calculations
User has a PowerLogic meter which has available utility registers
For example, assume the desired value requires a scale factor of 0.026 and a offset of -200: