The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The following error message appears during step 2 of the System Manager Software (SMS) 4.3 upgrade:
The PatchInstaller failed to complete successfully. Please re-run the install. Setup will now end.
The user is also running eSolutions software PRODUCTS such as Active Pager Module (APM) or Sequence of Events Recorder (SER).
Causes and Fixes
eSolutions services for either Active Pager Module, Sequence of Events Recorder, or both are running.
Stop all eSolutions services via the eSolutions Service Controller and re-run the SMS install.
Note: The eSolutions Service Controller can be access by double-clicking on the red dragon icon in the Windows task bar.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!