Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The following error message appears during step 2 of the System Manager Software (SMS) 4.3 upgrade:
The PatchInstaller failed to complete successfully. Please re-run the install. Setup will now end.
The user is also running eSolutions software PRODUCTS such as Active Pager Module (APM) or Sequence of Events Recorder (SER).
Causes and Fixes
eSolutions services for either Active Pager Module, Sequence of Events Recorder, or both are running.
Stop all eSolutions services via the eSolutions Service Controller and re-run the SMS install.
Note: The eSolutions Service Controller can be access by double-clicking on the red dragon icon in the Windows task bar.