Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
A user when configuring the delay for onboard alarms in a Power Meter or Circuit Monitor, would like to know the units associated with the pickup and dropout values.
Circuit monitor/ power monitor settings
Associated units and values
For standard speed alarms, the delay is defined in seconds.
For high speed alarms, the delay is defined in increments of 100ms.
For disturbance alarms, the delay is defined in cycles.
For example, a delay of 5 for standard alarms equates to 5 second. For high speed alarms, a delay of 5 equates to 500ms. For disturbance alarms, a delay of 5 equates to 5 cycles.