Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
What is the industry standard for current transformers (CTs) and potential transformers (PTs)? What is representation of letters H, X and S?
3090 SCCT, current transformers (CTs), and potential transformers (PTs)
Installation of CTs and PTs.
Installation and wiring of CTs and PTs
*Warning: Installation and maintenance of this device should only be performed by qualified, competent personnel that have appropriate training and experience with high voltage and current devices. Failure to follow the instructions / warnings in the Meter Installation Guide can result in permanent damage to the meter, severe injury or death.
The industry standard for current transformers (CTs) and potential transformers (PTs) are as follows:
The Primary or Line side is designated with the letter 'H'.
The Secondary or Load side is designated with either the letter 'X' or 'S'.
X1, S1, or H1 is the positive wire.
X2, S2, or H2 is the negative wire.
Schneider Electric model SCCT current transformers identify the X1 wire as WHITE and the X2 wire as BLACK.
Note: Check with the most recent CT or PT cut sheet to verify color designation.