Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
If one device has a timestamp of 8:00:00am and the other device assigned to the virtual source has a timestamp of 8:00:01am the virtual meter will not totalize at 8:00:00am because the virtual meter sees the second timestamp as a gap in the data. Make sure that jitter correction is turned on for the sources to make sure that all the timestamps will be on the hour readings in the virtual source. Jitter Correction can be turned on in the ION EEM Admin Tool under the Data Import page.
Date Created: July 22, 2009
Last Revised: July 22, 2009
Original Author: MN
All content © 1992-2009 Schneider Electric