Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
This happens because some of the output values for this meter have the special character '#' in the label names. On the 37xx meters this cannot be changed. In order to get around the issue, link these outputs up to an arithmetic module in the VIP. Change the outputs of the arithmetic module to something without special characters (only letters and numbers) and then link the Vista diagram up to the newly created VIP arithmetic module outputs.
Date Created: October 24, 2008
Last Revised: May 6, 2009
Original Author: MN
All content © 1992-2009 Schneider Electric