Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
When sending the .dcf meter template file into the meter using ION Setup, it will return an error message and say "Unable to download dcf(xml) file to a non-RMP device"
Causes and Fixes
Rapid Meter Programming (RMP) is not supported in ION7500RTU meters, hence the .dcf files can not be sent to the meter using ION Setup. Instead, simply paste the .fwn version of the meter template file using ION Setup. ION Setup will treat this fwn file the same as the .dcf file with meters that support RMP. Please see the template file attached.
(Removed File URL: 198385_B79E/7500-RTU_V1.1.0.fwn)(Removed Image URL: /PubResEXPORT.nsf/2b87ee90be777fc085257c28006ee4ef/f23cc1f31e56d096c12575a70052a263/fl_block_5/0.56E?OpenElement&FieldElemFormat=gif)
(Removed Image URL: /PubResEXPORT.nsf/2b87ee90be777fc085257c28006ee4ef/f23cc1f31e56d096c12575a70052a263/fl_block_5/0.26EE?OpenElement&FieldElemFormat=gif)
Date Created: March 3, 2009
Last Revised: April 29, 2009
Original Author: KG
All content © 1992-2009 Schneider Electric