Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
ION 6200 series Power Meters do support THD functionality with Enhanced Package 2, however, due to limitations in available memory space, this feature is not available when the Volts Mode is set to Delta or Delta Direct. Hence, when the ION6200 meter is used in these Volts Modes, the meter will return '0' for THD values both on the front panel display and through communications with the device.
It is recommended to use the PM750 or PM800 series meters instead if it is desired to get the THD values used in Delta or Delta Direct configurations.
Date Created: April 2, 2009
Last Revised: April 28, 2009
Original Author: KG
All content © 1992-2009 Schneider Electric