Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Below the rated OPERATING temperature (-20ºC = -4º Fahrenheit), the correct operation of the meter cannot be guaranteed. Accuracy will suffer and depending on how low the temperature gets, different components may not function correctly. There arent specific temperature values for anything other than the LCDs, which operate to -25ºC.
Below the rated STORAGE temperature (-40ºC = -40º Fahrenheit), all components will be suspect and the meter may not work at all. Damage is possible to the display and other components.
If the temperature only dips below operating temperature occasionally, and for short periods, it should be fine. Continued operation at cold temperatures or cold startups may cause problems for the meter.
Last Revised: April 9, 2008
Applies To: ION 6200
Original Author: KG
All content © 1992-2008 Schneider Electric