Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
EGX100 termination dip switches are set to "on" for termination
When the termination is enabled (On), the EGX applies a 120 ohm resister across the RS485 terminals.
In a 2 wire application the 120 ohm resistor is connected across the positive (+) and negative (-) terminals (In this 2-wire mode the RX+ and TX+ are jumpered together and the RX- and TX- are jumpered together).
In the 4 wire application mode two 120 ohm resistors are connected. One is connected across the transmit plus (TX+) and transmit negative (TX-). The other is connected across the receive plus (RX+) and the receive negative (RX-).
The modbus standard specification requires both sides of a modbus daisy chain to be terminated.