The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
A CM2000 is connected through an EGX200 and when you try to move the device from Setup Data Mismatch to selected devices in the System Device Status screen under the Database Status tab and update the database the PowerLogic Setup Utility shuts down. If you try to go into the setup screens for the meter the screen is greyed out. The device gets instantaneous readings in SMS and you can read the registers through SMS on the device. All of the communications parameters appear to be correct.
Causes and Fixes
Check to see if the EGX200 is version 5.0. If this is the case upgrade the firmware on the EGX200 to resolve this issue.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!