Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
A CM2000 is connected through an EGX200 and when you try to move the device from Setup Data Mismatch to selected devices in the System Device Status screen under the Database Status tab and update the database the PowerLogic Setup Utility shuts down. If you try to go into the setup screens for the meter the screen is greyed out. The device gets instantaneous readings in SMS and you can read the registers through SMS on the device. All of the communications parameters appear to be correct.
Causes and Fixes
Check to see if the EGX200 is version 5.0. If this is the case upgrade the firmware on the EGX200 to resolve this issue.