Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The ION meter configured as Modbus slave can easily provide data to its master using Modbus slave modules. It doesn't make any difference if the master is another ION meter (using "Modbus Master Device" modules) or a third party product.
This articles detail the actions for the slave ION meter to receive information from the master.
Facts and Changes
Modbus, slave, ION Meter
Causes and Fixes
ION Modules offer the availability for a slave meter to accept inputs. To do so, create External Pulse, External Boolean or External Numeric modules, depending on the type of information you need to import. All these "External" modules are available over Modbus. The map is given in the "Common_Modbus_Registers.pdf", starting on page 27. These modules can be modified over Modbus the same way as in a Vista diagram.
For example, to trigger the "External Pulse #1", write the number "1" at the Modbus address 42001.
To change the value of the "External Boolean #1", the address is 42201. Write "0" to turn to OFF state, and write "1" to turn to ON state.
To write a value in "External Numeric #1", simply write a value at the Modbus registers 42301 and 42302. The number needs to be in Signed Integer 32-bits format (42301 is the high order word, 42302 the low order word).
Note: Standard Security must be disabled for changes be made to the meter. If Standard Security is enabled, a "Modbus Exception # 3 - Illegal Data" message will be received when trying to write the register.
The ION 6200 doesn't include ION modules. For Modbus communication with an ION 6200 refer to:
Last Revised: November 18, 2010
Original Author: BB
All content © 1992-2010 Schneider Electric