Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
A distributed control system (DCS) refers to a control system usually of a manufacturing system, process or any kind of dynamic system, in which the controller elements are not central in location (like the brain) but are distributed throughout the system with each component sub-system controlled by one or more controllers.
When using Modbus TCP, ION meters allows the use of a hard coded 100 as the Modbus / Unit ID. Since ION devices do not support changeable Modbus Device IDs when using the Modbus TCP protocol, the software will have to use ID 100 and the IP address nomenclature to identify the device. Some DCS do not allow multiple slave devices to use the same Modbus / Unit ID, therefore it may not be possible to have multiple ION Modbus slave devices on a single Network in a DCS. Please check this with the DCS manufacturer.
Last Revised: November 22, 2007
Applies To: ION 7550 / 7650 / 8600 / 8800
All content © 1992-2007 Schneider Electric