Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
DNP3.0 requires a unit ID even if it is over ethernet.
ION 7500, ION7600
The framework in an ION7600 does not allow you to set the DLAddress for ethernet (which is essentially the unit ID).
NOTE: all devices and COM ports must have unique device IDs, and all operate at the same baud rate.
- Set COM2 to Ethergate
- Connect the twisted shielded pair (RS485) between COM1 and COM2
- Set the protocol on COM1 to DNP3.0 then set the unit ID to the desired number.