Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The Shield and GND (ground) connections are internally connected in an ION meter using a diode bridge.
This is the best wiring solution for connecting a 3-Wire RS-485 device to an ION Meter (COM1 or COM2).
NOTE: The fourth wire (Shield) should still be present in the communication wire bundle, but left unconnected at the ION meter.
Last Revised: October 15, 2007
All content © 1992-2007 Schneider Electric
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!