Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
If the load which the CM2000 is monitoring losses voltage on any ONE phase, the CM2000 has the ability to alarm on this. The specific alarm is Voltage Loss (Alarm #31), which is an alarm that will become active when any ONE phase drops below the user-defined pickup value. The alarm will NOT become active is all three phases drop below the pickup value.
This specific alarm can be associated with the operation of a relay output on a IOM, if installed.
Note: If the meter losses control power, there is no ability to signal the Voltage Loss alarm unless the CM2 Ride-Through Module is installed.
Note: The same applies for subsequent Circuit Monitor models and PM800 series meters. These meters however have no ride-through module option.