The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
A CM2000 series circuit monitor is displaying alarm code 47 on the front display.
CM2000 Series Circuit Monitor
Alarm code 47 is defined as "Suspended Sag/Swell". The alarm is to identify an excessive number of Sag/Swell events being generated on the meter.
An "excessive number" of Sag/Swell events is defined as:
More than 48 events total from all Sag/Swell Alarms in any 500ms period, or more than 6 events from any single Sag/Swell Alarm in any 500ms period.
Alarm code 47 is active when event 47 is true which occurs when register 2038 on the meter is not equal to zero. If the user disables alarm 47 without clearing Register 2038, the alarm will immediately be re-enabled and asserted as true.
To clear alarm 47, write a 0 to register 2038.
To learn how to read and write registers using the front panel of the CM2000 series meter, please refer to KB article FA211912.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!