Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
A CM2000 series circuit monitor is displaying alarm code 47 on the front display.
CM2000 Series Circuit Monitor
Alarm code 47 is defined as "Suspended Sag/Swell". The alarm is to identify an excessive number of Sag/Swell events being generated on the meter.
An "excessive number" of Sag/Swell events is defined as:
More than 48 events total from all Sag/Swell Alarms in any 500ms period, or more than 6 events from any single Sag/Swell Alarm in any 500ms period.
Alarm code 47 is active when event 47 is true which occurs when register 2038 on the meter is not equal to zero. If the user disables alarm 47 without clearing Register 2038, the alarm will immediately be re-enabled and asserted as true.
To clear alarm 47, write a 0 to register 2038.
To learn how to read and write registers using the front panel of the CM2000 series meter, please refer to KB article FA211912.