Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
There is no way to perform a manual waveform trigger with IONSetup 2.0
ION Setup 2.0,, ION7500, ION7550,ION 7600, ION7650, ION8400, ION8500
By default IONSetup does not provide a way to manually trigger a waveform.
The recommended solution is to upgrade to aversion of ION Setup 3.0 which has included the manual waveform trigger.
If an upgrade to ION Setup 2.0 is not possible then the below solution will work:
What ION Setup displays is determined by the setup tables. Look in the IONSetup/tables directory and you will see one subdirectory for each meter type. Inside you can find a file called Enables.pml.
Edit this Enables.pml:
1. Replace the Rows=5 line with Rows=6
2. Add into Page1 after the R5C4 entry:
The handle 0x68b9 is the handle of the External Pulse module that triggers waveforms on the 7500/7600/8400/8500 meters.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!