The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The Auto-Disconnect feature does not work with a custom Log Inserter when the Log Acquisition module is disabled.
Facts and Changes
Connection schedule, Auto-disconnect, Custom Log Inserter, Log Acquisition module
Causes and Fixes
When the Log Acquisition module is disabled and a connection is made to a site, that site does not disconnect after all logs have been retrieved even when the Disconnect from each site as soon as all data has been retrieved option is selected.
All logs requiring retrieval must be up to date for the Auto-Disconnect feature to work.
From the Log Acquisition module description in the ION Reference:
When [the Enable] input is set to on, the module is enabled; when it is set to off, the module is disabled and logs are not uploaded.
The Log Acquisition module is not considered caught up when the logs are not updated.
All content © 1992-2005 Power Measurement
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!