Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
No, it is not possible to have negative Voltage Unbalance reading from a Series 800 Power Meter or a Series 3000/4000 Circuit Monitor. All voltage unbalance readings will be an absolute value expressed as a percentage of unbalance. Voltage Unbalance is calculated using the following formula: Vunbalance = [(Vavg-Vphase) divided by Vavg].
It is possible, however, to have negative Voltage Unbalance readings if the device is a Series 600 Power Meter or a Series 2000 Circuit Monitor. These devices express Voltage Unbalance as a positive or negative percentage.
In general the absoute value of any Voltage Unbalance larger than 2.5 can cause heating in motors.
Version: Series 600 Power Meter
Series 800 Power Meter
Series 2000 Circuit Monitor
Series 3000 Circuit Monitor
Series 4000Circuit Monitor
© Schneider Electric 2005
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!