Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
No waveforms are displayed in Vista when a manual waveform trigger is performed.
StruxureWare Power Monitoring (SPM)
Power Monitoring Expert (PME)
ION 7500, ION 7550, ION 7600, ION 7650, ION 8400, ION 8500
ION7500, ION7550, ION7600, ION7650, ION8400, ION8500
Vista Manual waveform trigger
The manual waveforms triggers for some ION meters have a preset sampling frequency of 7680 (128samples/cycle x 60Hz) while in DEMO mode.
When viewing waveforms, there are filters to differentiate between sags (sampling frequency < 2000) and transients (sampling frequency > 15000). All waveforms that fall between these filters are left out; therefore, the manual waveform triggers are not displayed.
Edit the filter on these waveform logs to include the sampled waveforms from the manual waveform trigger:
How to Add Waveform Log Filters to include Manual Waveform Triggers1. Confirm that Show Toolbox is checked in Options then open a Vista diagram with the waveform log viewer. Right-click the log viewer to open Properties.
Note: Designer must be closed in order for vista to update correctly.